Control Panel Cooling units Technical Information
3-1. Maintaining a proper environment inside a control panel
This section describes the need for environmental measures inside the control panel and how to implement these.
(1) Evolution of FA and improved performance and functionality of control equipment
In recent years, FA-Factory Automation has become common in production facilities. In the factory, robots and automatic machines are situated not only on the first floor, but also cramped onto the second floor. This evolution can be said to be a natural flow in order to reduce cost by mass production.
However, while low-cost mass production may be possible, other disadvantages may also arise e.g. the heat emitted by robots and automated machines can adversely affect control equipment. In particular, as electronic devices become smaller and more functional, machines and panels are further reduced in size. Heat generation itself is on the rise, further affecting electronic devices.
Although control equipment which have become higher in speed, performance, and functionality offer the advantage of improved efficiency and processing speed, they can be said to suffer from the disadvantage of having to be installed in an environment where “heat, dust, and moisture” are not suitable for the control equipment.
(2) Impact of control equipment problems
Let's take a look at how control equipment problems are affecting actual production activities then.
For example, assume that a control board has stopped. Even if it is only for 10 to 20 minutes, as the production line is integrated from the pre to the post processes, an interlock will also be applied on the lines before and after the control panel which stopped, thereby stopping the machines.
In addition, if furnaces and other equipment are stopped, restoration is likely to take one to two hours for sure. In other words, taking into account the restoration of the lines before and after due to the failure of a single control panel, it is likely that a loss of around two hours will occur.
For example, assume that an inverter has stopped. Naturally, if you replace the inverter, you will incur the purchasing cost of the new inverter. Replacing the board alone would probably cost tens of thousands of yen.
If you do not have any spare parts, it may take several days or even weeks depending on the situation. If it is an old inverter, the production may also have been discontinued. Separate charter expenses will be required for remote locations or emergencies etc. Furthermore, if you hold stock in anticipation of an emergency, your inventory assets will increase. When it comes to increasing the number of maintenance personnel for preventive maintenance and periodic inspections, it is important to be prepared for significant costs that will lead to increased labor costs.
The issues above are happening in production sites on a daily basis. The impact of heat and humidity which often lead to sudden stoppages of machines and control panels are introduced in the next section.
(3) Impact of heat on equipment
Data has also proven that the failure rate of semiconductors and electronic components is greatly affected by heat, thereby shortening the life span. Graph (1) shows the change in the outside temperature and the temperature inside the control panel of a certain automobile manufacturer. A temperature difference of about 15 to 20 °C has occurred from the start to the end.
This way, the life of a capacitor used in an electronic device is greatly reduced as shown in Graph (2) when the temperature inside the board increases from to 55 °C or 60 °C.
Graph (2) is known as the “10 °C Double Law” because it shows the relationship between the life of an electrolytic capacitor and the ambient temperature. At a temperature of 30 °C, the life of an electrolytic capacitor is almost 80,000 hours, but this drops to 40,000 hours at a temperature of 40 °C. In other words, the life span is halved. In addition, at a temperature of 60 °C, the life span is about a quarter or 10,000 hours. The life span of semiconductors and electronic components is also greatly reduced by heat.
The life span is halved for every 10 °C rise in temperature
10 °C Double Law
The graph on the left shows the relationship between the life of electrolytic capacitors used in electronic devices and the ambient temperature.
When the ambient temperature rises by 10 °C, the life of the electrolytic capacitor is halved.
Due to the miniaturization and improved performance of electronic devices, the amount of heat generated is on an uptrend. Furthermore, the control panels that house these devices are also decreasing in size, so the temperature inside a control panel that is not equipped with any countermeasures is expected to rise higher than ever before.
In addition, Graph (3) shows the relationship between the failure rate of a semiconductor and the ambient temperature, which is known as the “Arrhenius Rule”. According to the graph, the failure rate is very small at a temperature of 30 °C or lower but it rises to 1 at a temperature of 40 °C. When the temperature reaches 60 °C, the rate increases from 10 times to nearly 30 times, and at 80 °C, it increases from 100 times to nearly 300 times all at once. It is well known that the failure rate of semiconductors and electronic components will increase dramatically as the temperature rises.
Failure rate increases at an accelerated rate together with a rise in the ambient temperature
The graph on the right shows the relationship between the ambient temperature of a semiconductor and the failure rate.
If the relative failure rate at 40 °C is assumed to be “1”, the rate will increase exponentially to “10” at 60 °C and “100” at 80 °C.
It is also known that the permanent cooling of control devices to continuously ensure the stable operation of production lines will become an important factor in future.
(4) Impact of moisture on equipment
Together with heat, moisture is one of the causes of control equipment problems. Here, we will consider how moisture affects control equipment.
There are many joints in control equipment. And the arch enemy of the joints is moisture. Graph (4) shows the relationship between corrosion and relative humidity, indicating that corrosion progresses rapidly when the humidity exceeds 60%. In Japan, the humidity level is usually known to be about 70%, so measures against humidity in control devices are extremely important. In addition, it is said that corrosion progresses faster as the temperature increases, so heat countermeasures can be considered as issues that must be considered at the same time as humidity countermeasures.
(5) Conventional countermeasures and their problems
The effect is largely dependent on the surrounding environment.
The effect is greatly influenced by the surrounding environment, and a huge effect cannot be expected when the outside air temperature is high. In addition, as outside air is sucked into the panel by the panel fan, “dust” and “oil mist” infiltrate the panel, causing problems in some cases instead.
There is no effect when the temperature of the outside air is high.
Unlike the fan for the panel, heat can be dissipated while the control panel is still in a sealed condition, but since the heat is dissipated using the temperature difference between the inside and outside of the panel, a significant effect therefore cannot be expected when the outside air temperature is high. Caution is required because the capacity may drop in some cases in summer.
Condensation may occur because cooling occurs rapidly.
Although a spot cooler is used as an emergency measure, it is originally designed for rapid cooling by the operator, so there is a possibility that condensation may occur when cooling electronic devices. In addition, it is not possible to prevent dust or oil mist as the panel is exposed to the outside.
There is a difference due to the distance and temperature unevenness occurs.
Due to the distance from the air conditioning and the amount of heat generated inside the panel, it is difficult to control the individual temperature for each control panel, resulting in extremely uneven cooling in the method. In addition, it is not suitable as an emergency heat countermeasure in the summer because it takes time to carry out the branching work of the cooling duct.
(6) Advantages in using a control panel cooler
1) Cooling effect
On the previous page, the spot cooler is assumed to have a low discharge temperature, but is it the same for the control board cooler? Some of you will probably think so. It is said that a typical spot cooler has a discharge temperature difference of 15 to 20 °C (the temperature difference between air being sucked in and air being cooled and blown out). Applying this temperature difference to a control panel cooler, condensation may occur when it is used under typical summer temperature and humidity conditions in Japan. (Graph ⑤)
For this reason, Apiste kept the discharge temperature difference to less than 8 °C on the assumption that the humidity is 60% of the average summer humidity in Japan, and stuck to its proprietary “mild cooling design” which will not allow condensation to occur. Condensation is prevented by cooling the air slowly while dehumidifying it. The components that make up the refrigeration cycle were reviewed one by one and adjustments were made to the design of Apiste’s proprietary refrigeration circuit. As a result, cooling that is gentle on electronic devices is realized.
2) Dust prevention effect
Due to its structure that completely separates internal from external air, a control panel equipped with a cooler turns into an independent sealed state spatially, which has a dust prevention effect that is unlike a cooler fan or the introduction of external air etc. This is why a control panel cooler is introduced in an environment where there is a lot of oil mist and dust.
3) Dehumidifying effect
When air containing moisture passes through a cooling coil cooled by a refrigerant, the moisture condenses due to the temperature difference on the surface of the cooling coil, and the water generated then is discharged outside. This process is known as dehumidification. A control panel is a product to improve the control panel environment so as to prevent not only heat problems but also problems caused by moisture and dust.
Previous item: 2-2. Refrigerant
Next item: 3-2. Precision air conditioners (TCU/ECU) and clean rooms
We're here to give you quick answers to your questions.